Your thermostat has the ability to reset all settings to the factory defaults. If you are certain you want to do this: In standby mode(when thermostat is turned off), press and hold button and for 5 seconds until RES is shown on LCD.Configure the menu
Resetting factory defaults
Press or once, you will see set temperature flashing. Use or again to adjust to the temperature you want your room to maintain. Press button to accept and exit.
Buttons and LCD displayButtonsPress &#x 5 s;ìon;
s00;Press 5 secondsTurning on/off thermostatMenu buttonIncrease the set valueDecrease the set valueLock /unlock buttonsReset to factory settings(when thermostat is turned off) +
The buttons are locked.Displays when heating is activeSetback mode
SymbolDescriptionSet temperatureSet At
Sensor selection. This thermostat is a combination model allowing you to choosebetween 3 different models. (A, AF,F )A model: air only, with built in sensorAF model: air & floor, with both built in and remote sensorF model: floor only, with remote sensorPress andhold button for 5 seconds. Now you can see Menu 01, t proeceed to other menu, press button again. T exit menu, press buttonFirst turn off the thermostat using the on/off buttonMenu # 01Switching differential.Calibrate the room temperature. This feature is used to compensate for any differenceCalibrate the floor temperature. This feature is used to compensate for any differenceSet the floor temperature limit.Select temperature format 0607080903040502Feature DescriptionFactory DefaultFeature Value0°C40 °C4°C10°C35°C2°C~ 7°C10°C~ 20°C20°C~ 35°C20°C ~ 40 °C °C / °F °CA / AF / F A Press or to selectThe numbers of degree difference before switching.between the displayed room temperature and a thermometer. between the displayed floor temperature and a thermometer. This feature is to protect the floor surface. °C or °F. The default is 1°C which means the thermostat will switch the heating on 0.5°C below the set temperature and will turn it off 0.5°C above the set temperature. With a 2°C differential, the heating will switch on 1°C below the set temperature and will switch off 1°C above the set temperature. 1°C1°C ~ 5°C-5°C ~ +5°C0°C-5°C ~ +5°C
Installation and Wiring
Carefully separate the front half of the thermostat from the back plate by placing a small flat head terminal driver into the slots on the bottom face of the thermostat. Carefully unplug the ribbon connector which is plugged in to thPlace the thermostat front half somewhere safe. Make the wiring connections as Screw the thermostat back plate on to the back box.shown in the diagram below.Re-connect the thermostat ribbon cable and clip the two halves together.
CS-11 LCD Digital Setback Thermostat
Swiched live output
230V ~ 50Hz LN
Liktemials 1to 3 r230VAlie output
Registered Address: 6 Tannery Yard, Witney Street, Burford, Oxon., OX18 4DWTel: 01993 824900 : www.emmeti.co.uk : e: email@example.com
This gives you the option to limit the minimum set temperatureThis gives you the option to limit the maximum set temperature 1. Please ensure that the electrical wiring of the installation and connections to and from the thermostat and any remote senso Wiring Regulations.2. The thermostat must be wired to the electric mains through a switch capable of disconnecting all poles compliant with the cu3. Before commencing work on the installation, the electricity supply must be disconnected.
WARNINGPlease Note: one of the following error messages will appear if one of these problems occur:E0, meaning the internal sensor is broken, short-circuit or not working properly.E1, meaning the floor sensor is broken, short-circuit, not connected, or not working properly.