A range of flexible conduit with an internal diameter of between 19mm and 23mm. To protect and sleeve the pipe through areas where heat emission is not required.
Please refer to the Emmeti Price List or the ‘Downloads’ section below or contact the office on 01993 824900 for technical details.
InformationEmmeti Pricelist_2017_UFH Pipes Fittings_Pipe Conduit
Emmeti Underfloor Heating Manifolds Sales Brochure
Product and system guide with range information, product features and examples for Under Floor Heating applications
What is crimp fitting or crimping?
There are many different systems on the market. Generally in the UK we use press fittings, which are a form of crimping. Connection is reached by pushing the outer sleeve to pipe, compressing it between the sleeve and the inner brass piece. This is achieved using a mechanical press tool. Emmeti offer a range of these, please ask for further information.How do I connect 22mm Hep2O pipe to your 1” manifolds?
Please purchase U9240018 22mm x 1” BSP Male copper adaptor. Ensure you follow the pipe manufacturer’s instructions on how to connect to 22mm copper adaptors.Are you able to join pipes under the floor?
This is achievable; you must ensure the joint is sealed with a protective tape (permanent adhesive like duct tape) to ensure screed does not seap in to the monoblocco pipe connector, as this will erosion of the seals over time, and perhaps create leaks. However where possible this should be avoided.How do I remove permanent airlocks in line in a pipe that is higher than the existing system air vents?
If the pipe is exposed, you can cut into it, and place a tee-piece (code 28103200), with two inline 24x19 monoblocco threads and a 1/2" FBSP connection, facing this upwards (fitted as an inverted tee). Choose monoblocco connectors from our range to match your pipe (take care of the pipe wall thickness). Then screw in a manual air vent 00400004 into the tee.Does Emmeti offer a pipe repair coupling?