Provides heat metering where fitted without manifolds. Cabinets are 600mm width with DN15 and DN20 options. Principal connections: 3/4”F and are suitable for connection on the left side of the system. Suitable for installation in a 120mm partition.
Can you advise which pipe goes where on an energy meter?
The heat meter (like a water meter) is located in the return line and the tee holder of the temperature probe is located in the flow line.Can you tell me what the connection size for an energy meter is?
It varies by each energy meter. You buy the meter based on DN size and match up to the tails (pipe union connections). The connections on the body of the meter are always 'bigger' than the final connection to the pipe. When you use the pipe union connections kit - e.g. a DN15 body has a 3/4" body connection - needs a 3/4"F x 1/2"M connection (02708098) - therefore if you want a 3/4" pipe connection, you need a 1" body DN20.