A wide range of Energy box cased models to provide heat metering together with distribution manifolds, from 2 -12 ways in cabinet width from 700mm – 1200mm. They are designed to be used to measure energy and provide distribution in apartments from a centralised heat source. 4-way zoning allows balancing for central building systems.Each module contains: Metal recessed cabinet with key operated lock, 4-way zone valve with manual by-pass; Y-type strainer; 2 drain/fill valves; manual air vent; remote probe socket; 4 DN20 ball valves with red and blue handles, 1 spacer ready for an energy meter, and hot and cold water meters.
Please contact the office on 01993 824900 for technical details.
Can you advise which pipe goes where on an energy meter?
The heat meter (like a water meter) is located in the return line and the tee holder of the temperature probe is located in the flow line.Can you tell me what the connection size for an energy meter is?
It varies by each energy meter. You buy the meter based on DN size and match up to the tails (pipe union connections). The connections on the body of the meter are always 'bigger' than the final connection to the pipe. When you use the pipe union connections kit - e.g. a DN15 body has a 3/4" body connection - needs a 3/4"F x 1/2"M connection (02708098) - therefore if you want a 3/4" pipe connection, you need a 1" body DN20.