A range of Under Floor Heating pipe accessories, including pipe shears, pipe cutters, leakage test plug for MultiLayer pipe and calibrator for MultiLayer pipe.
Please refer to the Emmeti Price List or the ‘Downloads’ section below or contact the office on 01993 824900 for technical details.
Product range includes:
Pipe Shears with Guide
Rotary Pipe Slices
Leakage test plug for MultiLayer Pipe – ½” F fitting
Flarer and calibrator for MultiLayer pipe
InformationEmmeti Underfloor Heating Manifolds Sales Brochure
Product and system guide with range information, product features and examples for Under Floor Heating applications
What is crimp fitting or crimping?
There are many different systems on the market. Generally in the UK we use press fittings, which are a form of crimping. Connection is reached by pushing the outer sleeve to pipe, compressing it between the sleeve and the inner brass piece. This is achieved using a mechanical press tool. Emmeti offer a range of these, please ask for further information.Can we connect to Wirsbro 20mm PE-X pipe?
Yes, use our 20mm Monoblocco connector 28100346 20x2mm. If you require to bridge between two different pipes, buy 28103080 24x19 straight adaptor, with the other Monoblocco matched to the different pipeHow do I connect 22mm Hep2O pipe to your 1” manifolds?
Please purchase U9240018 22mm x 1” BSP Male copper adaptor. Ensure you follow the pipe manufacturer’s instructions on how to connect to 22mm copper adaptors.Are you able to join pipes under the floor?
This is achievable; you must ensure the joint is sealed with a protective tape (permanent adhesive like duct tape) to ensure screed does not seap in to the monoblocco pipe connector, as this will erosion of the seals over time, and perhaps create leaks. However where possible this should be avoided.How do I remove permanent airlocks in line in a pipe that is higher than the existing system air vents?
If the pipe is exposed, you can cut into it, and place a tee-piece (code 28103200), with two inline 24x19 monoblocco threads and a 1/2" FBSP connection, facing this upwards (fitted as an inverted tee). Choose monoblocco connectors from our range to match your pipe (take care of the pipe wall thickness). Then screw in a manual air vent 00400004 into the tee.Does Emmeti offer a pipe repair coupling?